Overfill Alarm Station FA-AV
The Overfill Alarm Station, or Fil-A-Larm System, is constructed out of stainless steel, NEMA 4X rated moisture-proof and corrosion-proof enclosure, designed to be located near the tank fill terminal to notify of a potential overfill. It triggers a high-level alarm that alerts the filling operator that the tank is filled to its capacity.
The Preferred Fil-A-Larm system is installed in conjunction with underground storage tanks and above ground main storage tanks.
It is designed to be located near the tank fill terminal to notify of a potential overfill. It triggers a high level alarm that alerts the filling operator that the tank is filled to its predetermined capacity. When an overfill alarm occurs, the alarm bell sounds and the corresponding alarm light flashes. The bell is automatically silenced in 90 seconds or instantly silenced when the operator selects the “Alarm Silence” pushbutton. The visual alarm is highly visible even in direct sunlight. The enclosure top mounted flashing lamp is visible from 180°. A “Test” pushbutton is provided to verify the operation of the flashing alarm light(s) and bell. The alarm automatically resets when liquid level goes below the overfill alarm setpoint. A digital display of tank volume is available.
- Prevents Overfilling Of Fuel Oil Storage Tanks
- Includes 4" Weatherproof Bell
- Moisture Proof Stainless Steel NEMA 4X Enclosure
- 6" 86 dB Alarm bell
- 40 Watt Alarm Bulb
Enclosure: Stainless Steel 12" W x 12" H x 6" D, NEMA 4X Construction
Audible Alarm: 4" 92 db bell
Visual Alarm: Lens 3 ¼" H, 4 ⅜" Dia. With 40 Watt Bulb
Alarm Silence Button: Silences Bell (Auto Time-Out Also)
Alarm Test: Verifies Flashing Alarm Light(s) And Bell
Construction: The Model Fil-A-Larm system is surface mounted, NEMA 4 rated moisture proof enclosure. The box material is carbon steel. The interior is prime coated and painted with a durable white enamel
DOCUMENTS & DOWNLOADS
|Overfill Alarm Station FA-AV Stainless Steel - SPEC|
|Overfill Alarm Station FA-AV-SS - Catalog Cutsheet|
|Overfill Alarm Station Wiring Diagrams|